Issues with Wiring Outdoor Lights
Our expert, Randall Whitehead, IALD, troubleshoots a troublesome wiring issue with low voltage outdoor lights.
I installed new low voltage wire to my exterior light fixtures after an animal chewed through the old wire. After the sun set and the lights came on, they were only half power — if that. The transformer is not overloaded. The wires are connected properly. The lamps are new. What’s wrong?
If the fixtures all are at low output, you may have the incorrect voltage of lamps. See if you have 24V lamps instead of a 12V. (The boxes look the same.). Also, most transformers are multi-tap for numerous voltages. Make sure that you have connected to the voltage that matches the lamp voltage. If the fixtures are dimmer at the end of the run and brighter at the end closest to the transformer, then you may be using the incorrect gauge of wire, resulting in voltage drop. There could also still be a tear in the wiring, resulting in power “leaking” into the soil. Or your house may have been built over a graveyard like in “Poltergeist.” Make sure your daughter has not disappeared into the television.
Randall Whitehead, IALD
Lastest from ask randall
I noticed in your photo that you have blackout shades and no mirror over the vanity. Is it possible that you are a vampire? I'm not judging; just... read full story
There are companies that make a surface-mounted downlight that mimics the look of a recessed fixture. Take a look at the Traverse fixture from Sea... read full story
We do deal with a lot of buildings that have concrete ceilings. If your ceiling is higher than 8 feet, then doing a 2-inch drop to run wiring is a... read full story
Sponsored by Access Lighting, Antares, Kichler and Light + Building. Originally Live: Thursday, Oct. 10, 2013Recorded webinar now available for viewing on demand.Webinar... read full story
Sponsored by Access Lighting, Kichler Lighting, Kimberly LED Lighting, Auroralight and Antares Lighting. The lighting marketplace is changing more rapidly today than at any... read full story