How to Deal With Heavy Recessed Can Lights
Heavy transformers could spur the downfall of remodel recessed cans, unless you follow the advice of lighting expert Randall Whitehead, IALD.
Take a look at the "leg" located below the transformer. It helps keep the housing level in the ceiling. Photo by Dennis Anderson.
Randall, while installing a remodel-type recessed can, I noticed that the transformer is very heavy. The only support for the housing is a few clips. Will this cause the housing to pull out of the drywall over time?
Although remodel cans are a great idea, they are not all created equal. The basic concept is that you are able to cut a hole in the ceiling that is the same diameter as the housing. Through this hole you can feed the transformer, normally affixed to an armature, which has the housing attached to the other end of the arm. This configuration is true of most of the 4-, 5- and 6-inch diameter cans that are available on the market. Regarding the weight issue, it depends on whose remodel fixture you use. With many of the remodel cans out there on the market, you are stuck with a heavy transformer hanging off the end of the arm, which can stress the clips that hold the housing to the sheetrock. Better-designed remodel fixtures, such as the Halo H1499RT and the Lucifer DHM, have transformers on armatures like the rest, but they also have leg-like supports that counterbalance the transformer so that the weight is not carried by the housing. Go to www.cooperlighting.com (Halo’s parent company) or visit www.luciferlighting.com to see examples of what I am referring to. If the fixture you’re using doesn’t have such a device built in, put some sort of blocking under the transformer so that it lessens the possibility of torque. Electricians tell me that stacking pieces of sheetrock works well, or perhaps you could use a nice, firm block of fruitcake. After all, I am a strong advocate of creative reuse.
Randall Whitehead, IALD
Lastest from ask randall
We are dealing with this situation on a regular basis now. Many people who were early adopters of LED products did not have the range of color... read full story
It is not possible to put recessed fixtures into a concrete ceiling, but there are a few creative ways you can approach it. One possible solution is... read full story
You do have some pretty high ceilings there. I think you should consider using a fixture with a higher lumen output, something in the 800 lumen range... read full story
Sponsored by Access Lighting, Civilight, GM Lighting, Langlais Group Inc. and Nora Lighting. Date: Thursday, April 24, 2014, 2 p.m. ET Register for free here Webinar... read full story
Sponsored by Access Lighting, Antares, Kichler and Light + Building. Originally Live: Thursday, Oct. 10, 2013Recorded webinar now available for viewing on demand.Webinar... read full story
Sponsored by Access Lighting, Kichler Lighting, Kimberly LED Lighting, Auroralight and Antares Lighting. The lighting marketplace is changing more rapidly today than at any... read full story